The Extend-a-stay goes between the tank outlet (Valve) and whatever is screwed into it.. This should be BEFORE your electric cut off and before your regulator. Of course if the wires on the solenoid valve are not long enough this could be a problem, it retuires moving the regulator (And the solenoid valve) farther away from the tank's manual valve.
iRV2.com RV Community - Are you about to start a new improvement on your RV or need some help with some maintenance? Do you need advice on what products to buy? Or maybe you can give others some advice? No matter where you fit in you'll find that iRV2 is a great community to join. Best of all it's totally FREE!
You are currently viewing our boards as a guest so you have limited access to our community. Please take the time to register and you will gain a lot of great new features including; the ability to participate in discussions, network with other RV owners, see fewer ads, upload photographs, create an RV blog, send private messages and so much, much more!
I see, in a case like that your propane wholesaler is your friend.. I am willing to bet they have adapters to mate a POL male and female to the fittings on your valve and regulator.. In fact on the regulator side the odds of them having the needed fitting are 100%
Then that short length of copper would be replaced by the Extend-a-stay